Carefully read the contents of the wiring specification of the LED high bay emergency lighting,and strictly follow the wiring diagram. Non-professionals must not install it.
[av_heading heading=’High bay emergency lighting installation method:’ tag=’h2′ style=” size=” subheading_active=” subheading_size=’15’ padding=’10’ color=’custom-color-heading’ custom_font=’#5bba4a’ av-medium-font-size-title=” av-small-font-size-title=” av-mini-font-size-title=” av-medium-font-size=” av-small-font-size=” av-mini-font-size=” admin_preview_bg=”][/av_heading]
1, according to the internal space of the customer’s lighting can be done in the form of body, the emergency power supply is installed in the lamp bracket or the internal safety wiring of the lamp, the external appearance is convenient for the customer’s installation and use;
2, can also be made into an integrated emergency power supply, with white cold-rolled steel shell or waterproof plastic shell assembly, can be installed in the wall top, ceiling, wall in all occasions (costs in addition to accounting).
3, L” (FireWire), N (zero line) for the constant charge line must always pass, outside the connection can be controlled switches;
4, L (FireWire) is a constant lighting control line, can be connected to the wall switch to control the LED light on and off; when the light only to test the emergency power supply does not require constant light switch control can be Changming FireWire L and charge FireWire L” short Can always be powered on;
5, Please carefully read the wiring drawings and installation instructions before installing the test. Other wiring must be strictly in accordance with the wiring diagram to ensure that no error after the power test.
[av_heading heading=’High bay emergency lighting Usage Notice:’ tag=’h2′ style=” size=” subheading_active=” subheading_size=’15’ padding=’10’ color=’custom-color-heading’ custom_font=’#5bba4a’ av-medium-font-size-title=” av-small-font-size-title=” av-mini-font-size-title=” av-medium-font-size=” av-small-font-size=” av-mini-font-size=” admin_preview_bg=”][/av_heading]
1, please use the battery specified by the manufacturer, before use, please confirm that the wiring is correct and there is no loose phenomenon, and the positive and negative poles of the battery are forbidden;
2. If you need to complete the test process after the product test is not completed, please unplug the battery pack first, then make the emergency power supply completely shut off and then plug in the battery pack plug.
3, strictly in accordance with the wiring diagram wiring, overload and no load during the use and testing process (this product is designed with no-load protection, but in the event of electricity safety in case, it is recommended that customers do not empty);
4, when the power fails, all lights are off;
5, When the battery is shipped from the factory, it is in an uncharged state. Please charge it for more than 24 hours before use.
6, It is recommended that the customer should charge the battery for 48 hours when using or testing for the first time to ensure that the battery is fully charged and the battery is at its best;
7, all batteries should not be placed unused for a long time, especially the exhausted battery should not be idle for a long time, when not in use for a long time, please fully charge the battery (time can not exceed three months) during storage Note that the battery positive and negative lines can not Short circuit